ßäåðíà ô³çèêà òà åíåðãåòèêà
1818-331X (Print), 2074-0565 (Online)
Model of formation of in-core neutron detector signalV. I. Borysenko1,2,*, Yu. F. Piontkovskyi2, V. V. Goranchuk1
Abstract: Fuel rods linear power rate is one of the most important indicators of safety and operating reliability of VVER fuel. The article describes the evolution of implementation of in-core monitoring system (ICMS) power distribution control function for VVER core. It is shown that requirements for the data and accuracy of determining the power distribution have significantly increased in comparison with the first VVER projects. This work presents results of MCNP numerical simulations of the signal formation in the Self-Powered Neutron Detector (SPND), which is resulted from the activation of emitter’s nuclei under the neutron irradiation. It has been demonstrated that the main contribution (~75 %) to the SPND signal provide fuel rods of fuel assembly in which SPND is located, and the fuel rods of adjacent fuel assemblies contribute ~25 %. Also, the height-dependent contribution of fuel rod to SPND signal was determined. The simulation results allow calculation of the geometric factor, which determines the contribution of fuel elements to SPND signal, taking into account not only six closest fuel rods, as implemented in the ICMS now, but few adjacent rows of fuel rods. This approach will improve the accuracy of the geometric factor calculation. The obtained results indicate the need to consider the effect of the spectral characteristics of neutron field on the SPND signal.
Keywords: linear power rate, reconstruction of power distribution, self-powered neutron detector, activation of rhodium emitter, burning of rhodium emitter.References:
1. V.A. Khalimonchuk. Operation Software ICMS top level of VVER-1000 under implementation in Ukraine of the expanded program on diversification of nuclear fuel. Yaderna ta Radiatsiina Bezpeka (Nuclear and Rad³ation Safety) 1 (2015) 7. (Rus)
2. Central Spent Fuel Storage Facility. Preliminary safety analysis report. Chapter 8. Yadernaya bezopasnost' (Nuclear safety) (SSIC CSER, 2016) 54. (Rus)
3. VVER physics experiments: regular hexagonal (1.27 cm pitch) lattices of low-enriched U(2.4 wt.% 235U)O2 fuel rods in light water at different core critical dimensions. NEA/NSC/DOC/(95)03/IV. Vol. IV. LEU-COMP-THERM-064, p. 70.
4. M.M. Sapon, V.I. Borysenko. Determination of reactivity coefficients VVER 1000 in the code MCNP. Abstracts of XXIII Annual Sci. Conf. of the Institute for Nucl. Res. of NAS of Ukraine, 1 - 5 Feb. 2016 (Kyiv, 2016) p. 107. (Ukr)
5. Yu.F. Piontkovskyi, V.I. Borysenko. Influence of parameters of the core VVER-1000 to initiate a signal SPND. Abstracts of XXIII Annual Sci. Conf. of the Institute for Nucl. Res. of NAS of Ukraine, 1 - 5 Feb. 2016 (Kyiv, 2016) p. 104. (Ukr)
6. Yu.F. Piontkovskyi, V.I. Borysenko. Accounting emitter burnup od SPND in the problem of reconstructing the energy distribution on the core of VVER-1000. V Int. Sci. and Practical Conf. “Safety and Efficiency of Nuclear Energy” (Odessa, Ukraine, 5 - 9 Sept. 2016). (Ukr)
7. S.A. Tsimbalov. Features of rhodium neutron detector DPZ-1M. Preprint IAE-3899/4 (Moskva, 1984) 16 p. (Rus)
8. I.V. Shamanin, A.V. Kiselev, V.A. Lyzko. Control of energy distributions in the operation of a nuclear reactor using a self-powered neutron detector. Izvestiya Tomskogo politekhnicheskogo universiteta 316(2) (2010) 67. (Rus)
9. V.I. Borysenko. Spatial effects of the reactivity of a change in thermal-hydraulic and neutron-physical parameters of the VVER core. Thesis of Candidate of Science (05.14.03) (Leningrad, 1991) 136 p. (Rus)
10. V.A. Bragin, I.V. Batenin, M.N. Golovanov et al. In-core Monitoring System of NPP with VVER (Moskva: Energoatomisdat, 1987) 128 p. (Rus)
11. S.A. Tsimbalov, V.F. Shikalov, A.V. Craiko. Tests of in-core monitoring system at start-up nuclear power plants with VVER-440. Preprint IAE-3050 (Moskva, 1974) 24 p. (Rus)
12. Rules of Nuclear Safety of Reactor Units of Nuclear Power Plants with Pressurized Water Reactors. NP 306.2.145-2008. (Ukr)
13. J.F. Briesmeister (ed.). MCNPTM – A General Monte Carlo N-Particle Transport Code, Version 4C. Manual. Report LA-13709-M, 2000. 898 p. (Documentation for CCC-700/MCNP4C Data Package, Sec. 4).
14. NTS NNEGC "Energoatom". Development of a national settlement complex ICMS-M2. Protocol No. 3 on 11/16/2016. (Rus)